The gas pressure regulator RMG 300 is suitable for systems requiring dynamic control (furnaces for steam). The unit is also ideal for natural gas and all fuel systems that are non-aggressive. The unit has a broad input pressure array and an external or internal measuring device. Thanks to its interchangeable operational components, the actuator has high stress compensation and easy maintenance. The control system can also be attached to the device. Regulator Gas
RMG 300 is an integrated safety relief valve (SBV) for gas leakage, and is essentially a safety diaphragm with RMG 915 air vapor. The module is equipped with a single thermally controlled locking device (TAE) with a temperature sensor and driver storage metal. The metal seal at the inlet of the pressure regulator can also be replaced with this. The gas pressure regulators RMG 300 are designed to ensure that the outlet pressure within the tube system remains constant, regardless of changes in the distribution of fuel or changes in the supply level. The pilot and SAV elements are included in the RMG 300 gas regulator. The RMG 300 features a thermal shut-off system (TAE) as an option. After the related repair bolts have been loosed, the working components can be easily removed from the main valve body.
A modular design allows a rapid reconstruction in the event of an organization malfunction of the defective operating system with the operated replacement unit. The same applies to the unit’s leadership. This control system consists of a central valve with a valve base and a valve stand, a relief diaphragm and a diaphragm, a spring and a set-point adjuster measuring device. The SAV command and the corresponding K1a or K2a control units are the security shut down feature (SAV). The main valve body contains bore holes that allow the pilot and SAV to link the internal relationship of measurement. The internal connections are shut by balls pointing into the holes of the shaft when external measurement sheets are used.
For the pilot conform to the pressure system, the adjustable gastril is used on the central valve side. The gas leakage safety valve (SBV) can be placed on the control device. It is not required when a safety flash is fitted or when the ventilation valve RMG 915 is installed. It is not necessary.